TY - RPRT
T1 - Phasor Technology Applications Feasibility Assessment and Research Results Report
Y1 - 2008/06//
SP - 66
A1 - Manu Parashar
A1 - Wei Zhou
A1 - Dan J. Trudnowski
A1 - Yuri V. Makarov
A1 - Ian Dobson
KW - AA08-003
KW - CEC-003
KW - phasor measurement units (PMUs)
KW - Reliability Adequacy Tools
KW - RTDMS
KW - RTGRM
AB - Phasor measurement data provide precise real-time direct monitoring capability of the power system dynamics (beyond the static view currently available via SCADA) at a very high rate. They also have the capability of accurately estimating and dynamically tracking various system parameters that provide a quantitative assessment of the health of system under the current operating condition and the prevalent contingency. In particular, synchronized phasor measurements provide an accurate sequence of snap-shots of the power system behavior at a very high rate (30 samples per second) along with precise timing information. The timing information is essential for real-time continuous estimation of system parameters that classify the power system. A precise estimate of the load, generator and/or network parameters consequently provide the most accurate assessment of the system limits of the current operating system. This time series data along with real-time system parameter estimates based on the data can be utilized to improve stability nomogram monitoring, small signal stability monitoring, voltage stability monitoring and system frequency response assessment. A main advantage of such methodologies is that they can measure actual system states and performance and do not rely on offline studies for its assessment, nor do they rely on comprehensive system models, which can be outdated or/and inaccurate.
ER -
TY - RPRT
T1 - Probabilistic Load-Dependent Cascading Failure with Limited Component Interactions
Y1 - 2004/05//
SP - 4
A1 - Ian Dobson
A1 - Benjamin A. Carreras
A1 - David E. Newman
KW - AA01-001
KW - AARD
KW - CERTS
KW - System Security Tools
AB - We generalize an analytically solvable probabilistic model of cascading failure in which failing components interact with other components by increasing their load and hence their chance of failure. In the generalized model, instead of a failing component increasing the load of all components, it increases the load of a random sample of the components. The size of the sample describes the extent of component interactions within the system. The generalized model is approximated by a saturating branching process and this leads to a criticality condition for cascading failure propagation that depends on the size of the sample. The criticality condition shows how the extent of component interactions controls the proximity to catastrophic cascading failure. Implications for the complexity of power transmission system design to avoid cascading blackouts are briefly discussed.
DO - 10.1109/ISCAS.2004.1329957
ER -
TY - Generic
T1 - A Probabilistic Loading-dependent Model of Cascading Failure and Possible Implications for Blackouts
T2 - Hawaii International Conference on System Sciences
Y1 - 2003/01//
SP - 9
A1 - Ian Dobson
A1 - Benjamin A. Carreras
A1 - David E. Newman
KW - AA01-001
KW - AARD
KW - CERTS
KW - power interruptions
KW - RTGRM
KW - System Security Tools
AB - A model has been developed to study the global complex dynamics of a series of blackouts in power transmission systems. This model has included a simple level of self-organization by incorporating the growth of power demand and the engineering response to system failures. Two types of blackouts have been identified with different dynamical properties. One type of blackout involves loss of load due to lines reaching their load limits but no line outages. The second type of blackout is associated with multiple line outages. The dominance of one type of blackouts versus the other depends on operational conditions and the proximity of the system to one of its two critical points. The first critical point is characterized by operation with lines close to their line limits. The second critical point is characterized by the maximum in the fluctuations of the load demand being near the generator margin capability. The identification of this second critical point is an indication that the increase of the generator capability as a response to the increase of the load demand must be included in the dynamical model to achieve a higher degree of self-organization. When this is done, the model shows a probability distribution of blackout sizes with power tails similar to that observed in real blackout data from North America.
JF - Hawaii International Conference on System Sciences
DO - 10.1109/HICSS.2003.1173909
ER -